FG Wilson Generator Parts , Oil Pressure Sender p/n 622-333
Other thread size HWT switches are also available to supply.
Range of measurement: 0-150psi
Alarm Pressure: 0.15±0.02 Mpa
Over Pressure Safety:1.5MPa
Weight:0.12kg Height:6.00cm Width:7.00cm Depth:7.00cm
Connections to the oil pressure switch/sender (part no 622-333) on
FG Wilson generators are as follows.
Terminal G: Is the sender and wire “OP” should be connected to this terminal – with the wire
disconnected, the terminal should read close to 10 ohms to ground
with genset off.
Terminal WK: Is the switch and *wire “15” should be connected to this terminal – with the
wire disconnected, the terminal should read less than 1 ohm to
ground with genset off.
* Wire “15” will not be connected on 2300 & 2800 electronic
engines, since the engine’s Electronic Control Module will control
the low oil pressure shutdown.
Credit card on line is available.We also accept payment by
Paypal,T/T and Western Union.
This item have stock,so can delivery to you within 3 business days
after your payment cleared.If there is any import duties or
taxes,it is the buyer's responsibility.
We offer 1 year warranty for this product. If the product is out of
working order under proper usage per instructions manual within the
warranty period, please contact us to obtain a merchandise return
code and shipping instruction. Then, send it back at your shipping
After receiving your return item, it will take 7 days for
evaluation and investigation. A brand new replacement unit will be
sent to you at our shipping costs if it meets our warranty
By DHL/FEDEX/TNT(China Express),if you'd like use others,please
contact with us.
Customs would be less likely to impose taxes / duties on a small
parcel. However, it will be at your expenses if incurred.
Insurance is included in the Shipping & Handling costs you
Your satisfaction is our goal,please leave 4 or 5 star feedback
.Much appreciation in advance.
Please contact with us before leave Neutral feedback or Negative
feedback,we'll help you solve all the
problem.Otherwise we will not provide technical support, or other